:: Construction Code Authority :: 1075 Suncrest Dr, Ste A, Lapeer, MI 48446 Phone:810-667-0420~Fax: 810-667-2952
Submit your permit application online by using the Navigation bar on the left for the appropriate permit. You can also download the applications to your computer, complete, and return to C.C.A. at the address or fax number listed above, by clicking on a link below.
Ground Fault interrupters required on all residential outside receptacles, including garages and all residential bathroom receptacles, and kitchen receptacles.
Firestopping is required where holes are drilled through any plate and cold air return.
Service and rough inspections could be covered under one inspection on new built homes if ready. Additional inspection fee due if not inspected at same time. Addition and remodeling permits require (2) inspections (Rough & Final)
The electrical inspector will call Detroit Edison to release the service hook-up.
All Fixtures hung, lamps and plate covers installed for final inspection.
Pre-Manufactured home installation required (4) wire installation, from disconnect to service panel.
Pre-Manufactured home connectors used for two or three wire circuits need inspection before siding is installed.
Pre-Manufactured home - One time Use Plugs, Self Contained Power Connectors- If these connectors are used in any installation of a pre-manufactured dwelling unit, they shall be installed and inspected to manufactures specifications. If the installation is in a concealed area of the unit, an inspection will be required before cover.
Interconnecting smoke detectors wired 110 volt on all floors and in each bedroom or sleeping area.
Swimming Pool installation required in conduit where the wire enters and exits the ground. Ground fault interrupter required. Bonding with continuous #8 bare solid copper wire around pool, tied to pool on (4) sides, ladder, and diving board for all pools. On ground pools require (1) inspection (Final). In ground pools require (3) Inspections. (Underground, Bonding & Final)
Air Conditioning Units ONLY- Inspection must be scheduled within (2) weeks of the installation.
Generator manufacture's specifications booklet must be on site for inspector to approve installation.
Chimney's must be two (2) feet above any obstruction within ten (10) feet.
Switch for shut off must be installed adjacent to furnace.
LP Gas regulators MUST be placed (18) inches above grade.
All approved appliances must be installed according to manufacturer's specifications. Installation instructions must be on job when inspection is conducted.
Ventilation air required in house.
Combustion air required in the area of the furnace.
All exhaust fans must be vented directly outside in metal pipe.
One appliance per flue if one is a solid fuel appliance.
Solid fuel appliances must be installed according to manufacturer's specifications or to State of Michigan Mechanical Code and MUST have a UL label or Label of recognized testing lab. (2) Inspections are required (Rough & Final)